Daylight harvesting is the term used in sustainable architecture and the building controls and active daylighting industries for a control system that reduces the use of artificial lighting with electric lamps in building interiors when natural daylight is available, in order to reduce energy consumption.
System design and componentsEdit
Daylight harvesting systems are typically designed to maintain a minimum recommended light level. This light level will vary according to the needs and use of the space; for example, the commonly recommended light level for offices in North America is 500 Lux (or around 50 footcandles) on the desktop.
All daylight harvesting systems use a light level sensor, a photosensor, to detect the prevailing light level, luminance or brightness, in open-loop or closed-loop systems. In an open-loop system, the photosensor detects the amount of available daylight only, and can be positioned on the building's exterior wall or roof, or inside the building facing the window or skylight. In a closed-loop system, the photosensor detects the total photometric amount of light, from both daylight and electric sources in the space. For example, in an office a closed-loop photosensor can be positioned on the ceiling facing the desktops in order to detect the amount of light on the work surface, as placing the sensor on the desktop itself would be impractical. In both the open- and closed-loop configurations, the signal from the photosensor must be carefully calibrated to accurately indicate the effect of exterior daylight variations on the light level on 'important functions' areas in the space. 
Control modules and dimmingEdit
The signal from the photosensor is interpreted by a lighting control system module, an automated light switching device, in the electric lighting system which can reduce the electric lighting, by shutting off or dimming fixtures as appropriate. If the electric lighting is dimmable, then the artificial lighting may be continuously adjusted in proportion to the amount of daylight available. If the electric lighting is on-off only, then an electric lighting fixture or lamp must remain on at full output until daylight can meet the entire recommended light level for the space. Non-dimming variants include having multiple non-adjacent light fixtures such as alternate units in the ceiling 'grid layout,' or daylight source adjacent fixtures near windows or skylights, linked for module on-off switching. Another variant of on-off switching is step switching (sometimes referred to as "bi-level switching"), in which multiple lamps in a single light fixture can be switched on and off independent of each other. This allows for typically one or two steps between full output and zero.
Dimming systems are generally more expensive than on-off systems. They have the potential to save more energy, because they can reduce electric light output when daylight can only partially meet the needs of the space. However, dimming systems may also require a little more energy for their basic operation. If a dimming system is well-calibrated, the occupants of the space will not notice changes in electric lighting due to daylight harvesting, whereas they are very likely to notice the changes due to on-off or step switching.
Several studies have recorded the energy savings due to daylight harvesting. Energy savings for electric lighting in the range of 20-60% are common.
Savings are very dependent on the type of space the light harvesting control system is deployed in, and its usage. Clearly, savings can only accrue in spaces with substantial daylight where electric lighting would have been otherwise used. Therefore daylight harvesting works best in spaces with access to conventional or clerestory windows, skylights, light tube groups, glass block walls, and other passive daylighting sources from sunlight; and where electric lighting would otherwise be left on for long periods. Such spaces have included offices, atria, interior public multistory plazas and shopping mall courts, and schools.
It is too simplistic to try to increase energy savings by increasing the size of windows. Daylight over-illumination may cause glare for occupants, causing them to deploy blinds or other window shading devices, and compromising the daylight harvesting system. Even partially-deployed [[venetian blind]s can cut energy savings in half.
Impressive energy savings estimates may not be realized in practice due to poor system design, calibration, or commissioning. Systems that dim or switch electric lighting in a distracting manner, or that produce overall light levels that are perceived as too low, can be sabotaged by occupants.  (For example, simply taping over a sensor will create constant electric lighting at maximum output.)
Payback, and Drivers for AdoptionEdit
There is an incremental cost to daylight harvesting systems. Dividing this cost by the annual energy savings provides a "simple payback", the number of years for the system to pay for itself. The shorter the calculated payback period, the more likely it is that a building owner will invest in the system. Costs vary for a whole host of local factors, but generally if energy costs rise, or the cost of the control hardware and installation falls, the payback period will be reduced.
The green building-sustainable building movement encourages sustainable architecture design and building practices. Various green building ecolabel certification marks exist around the world, such as LEED, BOMA Best, BREEAM, HKBeam, and Green Star. All of these programs offer points for various building design features that promote sustainability, and certification at various levels is awarded for reaching a given number of points. One of the principal ways to gain points is through energy saving measures.
Therefore, daylight harvesting is a common feature of green buildings.
Thus green building practices are increasing the production of daylight harvesting components, leading to lower prices.
Many electric utilities provide financial incentives for their customers to save energy. One such incentive is rebates on daylight harvesting systems  , which also reduces payback periods.
In addition, energy codes and standards are beginning to address daylight harvesting. For example the California Energy Code Title 24-2008 recognizes primary and secondary daylight zones. At least 50% of the general lighting in primary zones must be controlled separately from other lighting, with automatic control required for larger zones. The code encourages automatic daylight harvesting in secondary zones by awarding power adjustment factor credits that can be applied to the lighting design. The 2009 International Energy Conservation Code (IECC) recognizes daylight zones around vertical fenestration and skylights, and requires that the lighting in these zones be controlled separately from the general lighting in the space. The 2010 ASHRAE 90.1 energy standard, expected to be published in the fall 2010, is also expected to address daylight harvesting. Meanwhile, ASHRAE 189.1, the first of a generation of sustainable construction codes, defines daylight zones and requires daylight harvesting control.
- ↑ ANSI-IESNA; Newsham, G. R. (2004). "American National Standard Practice for Office Lighting, RP-1". ANSI-IESNA.
- ↑ Rubinstein, F.; Ward, G.; Verderber, R. (1989). "Improving the performance of photo-electrically controlled lighting systems". Journal of the Illuminating Engineering Society, 18(1). pp. 70–94. http://gaia.lbl.gov/btech/papers/24871.pdf. Retrieved 06 September 2009.
- ↑ O’Connor, J.; Lee, E.; Rubinstein, F.; Selkowitz, S. (1997). "Tips for Daylighting with Windows". Lawrence Berkeley National Laboratory, LBNL-39945. pp. Chapter 8. http://windows.lbl.gov/daylighting/designguide/dlg.pdf. Retrieved 03 September 2009.
- ↑ Bierman, A. (2007). "Photosensors: dimming and switching systems for daylight harvesting". Lighting Research Center, NLPIP, 11(1). http://www.lightingresearch.org/programs/NLPIP/PDF/VIEW/SR_Photosensors.pdf. Retrieved 03 September 2009.
- ↑ Galasiu, A.D.; Newsham, G. R.; Suvagau, C.; Sander, D. M. (2007). "Energy saving lighting control systems for open-plan offices: a field study". Leukos, 4(1). pp. 7–29. http://www.nrc-cnrc.gc.ca/obj/irc/doc/pubs/nrcc49498/nrcc49498.pdf. Retrieved 15 August 2009.
- ↑ Galasiu, A.D.; Atif, M.R.; MacDonald, R.A. (2004). "Impact of window blinds on daylight-linked dimming and automatic on/off lighting controls". Solar Energy, 76(5). pp. 523–544. http://www.nrc-cnrc.gc.ca/obj/irc/doc/pubs/nrcc46780/nrcc46780.pdf. Retrieved 03 September 2009.
- ↑ HMG (2006). "Sidelighting Photocontrols Field Study". Northwest Energy Efficiency Alliance. http://www.nwalliance.org/research/reports/152.pdf. Retrieved 03 September 2009.
- ↑ Birt, B.; Newsham, G. R. (2009). "Post-occupancy evaluation of energy and indoor environment quality in green buildings: a review". 3rd International Conference on Smart and Sustainable Built Environments, Delft, the Netherlands, June 15–19. http://www.nrc-cnrc.gc.ca/obj/irc/doc/pubs/nrcc51211.pdf. Retrieved 03 September 2009.
- ↑ Baylon, D.; Storm, P. (2008). "Comparison of commercial LEED buildings and non-LEED buildings within the 2002-2004 Pacific Northwest commercial building stock". Proceedings of ACEEE Summer Study on Energy Efficiency in Buildings (Pacific Grove, CA). pp. 4.1–4.12.
- ↑ National Grid (2009). "National Grid’s lighting incentive and eligibility requirements manual for Massachusetts, Rhode Island and Nantucket customers, Design 2000plus Program". National Grid. http://www.nationalgridus.com/non_html/shared_energyeff_lighting_newconst.pdf. Retrieved 03 September 2009.
- ↑ "California's Energy Efficiency Standards for Residential and Nonresidential Buildings". 2008. http://www.energy.ca.gov/title24/2008standards/.
- Cost Effective Simplified Controls for Daylight Harvesting California Lighting Technology Center, University of California, Davis
- Daylight Harvesting Made Simple California Energy Commission
- Daylighting Whole Building Design Guide
- Daylight Harvesting Implementation by Rainbow Grocery Co-op
- National Research Council Institute for Research in Construction (NRC-IRC) Lighting Research
- Harvest Daylight and Reap Rewards by Daintree Networks
This page is being imported from Wikipedia, to create a Wikidwelling stub or article. These steps need to be completed: